ICP 100136 Blower Motor
NOTE: THIS PART IS NO LONGER AVAILABLE. CALL 734-326-3900 WITH MODEL AND SERIAL NUMBER FOR MORE INFORMATION.
- (1) - Blower Motor (100136)
- Manufacturer Part #: HE3J137N
- Horsepower: 1/2
- Voltage: 208/230
- Hertz: 60
- Number of Phases: 1
- FLA: 3.60
- Number of Speeds: 3
- Rotation: REV
- Capacitor Needed: 7.5/370
- Frame: 48
- Mounting Type: BAND/THRBLT/RES
- Shaft Diameter: 1/2"
- BearingType: SLEEVE
- Length: 5-1/2"
Note: Always check the blower wheel on your blower assembly. Bad or unbalanced blower wheels can cause premature motor failure due to vibration. If you are not sure what blower wheel fits your blower assembly, call us at 734-326-3900.
To prevent premature motor failure, it is highly recommended you change your capacitor along with your motor. Capacitors out of tolerance can cause motors to overheat and prematurely fail. If you are unsure of what capacitor is required for your unit, please call us at 734-326-3900.
Replaces Old ICP Part Numbers:
Fits ICP, Heil, Tempstar, Arcoaire, Comfortmaker, Snyder General, KeepRite and Day & Night Models:(Press ctrl + F to find model number below if you have any questions call 734-326-3900 for further information)
NRGF36DDB03, NRGF36DDB04, NRGF36DDH02, NRGF36DDH03, NRGF36DKB03, NRGF36DKB04, NRGF36DKH02, NRGF36DKH03, NRGF36EDB02, NRGF36EDB03, NRGF42DDB03, NRGF42DDB04, NRGF42DKB03, NRGF42DKB04, NRGF42EDB02, NRGF42EDB03, NRGH36DDB01, NRGH42EDB01, NRLF36DDB04, NRLF42DDB04,
What are the symptoms of a ICP AC Blower Motor not working?
Burning smell through vents. Humming and/or bearing noise. Breaker trips. Furnace turns off and does not restart. Motor is seized and cannot turn blower wheel by hand.
Technical Hot and Cold offers the ICP 100136 Blower Motor OEM replacement part for sale online and over the phone. Call (734)326-3900 to speak with a technician for additional information on each ICP replacement part.